Dome controlled by an IPX800 v3 and the IPX800 Clamshell ASCOM driver in San Pedro de Atacama (Chile). Video credit : Alain Maury, SPACE
Version 2.0.0 and above
Microsoft .NET Framework 4.5 or above
Plateform ASCOM 6.2 or above
Microsoft .NET Framework 4 or above
Plateform ASCOM 6.2 or above
Version of the IPX800: version 2, version 3 or version 4
The IPX800 can be controlled using two protocols: M2M (Machine to Machine) or HTTP (equivalent to a control by the web interface).
Note: In case of use of an X880 extension and a firmware version older than v3.05.46 it's recommended to use the HTTP protocol; the extensions do not always react properly to the M2M commands with older version.
IP address and port
IP address and port of the IPX800.
The default port numbers are: 9870 for M2M protocol and 80 for the HTTP protocol.
User and password
The user and password configured to access the web interface of IPX800.
When using the M2M protocol, the password is only required if the firmware version is 5.3.46 or higher.
Dome activated parts
With this option you can specify whether one or both parts of the dome have to be opened.
It is possible to open the two parts of the dome simultaneously or to open one part after the other.
If one of the relays is configured in pulse mode, the time required to open / close one part of the dome must be configured. It is recommended to specify a value slightly higher than the actual duration.
The abort mode allows to configure the behavior of the ASCOM Abort Slew functionality. The role of this function is to interrupt the dome slew. Three values are possible:
Not supported: this is the option to select if your system does not allow interruption. The call of ASCOM AbortSlew function will have no effect.
Open relay: Select this option if the interruption of the dome slew can be done by opening the relay.
Close relay: Select this option if the interruption of the dome slew can be done by closing the relay. This is for example the case for some garage door or portal opening system...
The initial state allows to specify the position of dome parts when connecting the driver. This can be useful if you manually open the dome before connecting to the driver. If a sensor is used, it will always override the state indicated in the configuration.
Relay and sensors settings
The driver allows to use sensors (e.g. magnetic sensor) to identify the dome position (open or closed). If you use such detectors, check the boxes and indicate on which entries of IPX800 they are connected.
These parameters define the behavior of the relay that have to be activated to trigger the opening and closing of the dome.
For each action, "open" and "close", specify the relay number to activate. If configured in pulse mode (from the IPX800 web interface) check the box. If this is not the case it is necessary to indicate the period during which the relay has to be activated.
Upgrade of the library used to communicate with the IPX800
Minimum .NET version is now 4.5.0
Various corrections and optimisations
The "Virtual" checkboxes are disabled when the IPX800 is not v4
Support of IPX800 v4 virtual outputs
Correction of a bug that prevent to write the ASCOM logs
Compatibility with IPX800 v4
Improvement of the state handling. In cases where the dome parts move at a very low speed, it could happen that the state remains open or closed during the opening/closing of the dome
Initial version, created from ASCOM driver template
This software is free, but any donation is welcome
Due to an error in the installer in versions prior to v2.0.0, it is recommended that you uninstall any older version before installing version 2.0.0 or later.